- Oct 30, 2017 -
Speaking of closed cooling tower in the use of the problems faced, first of all, we actually have to pay attention to it itself is to face the uneven distribution of water (pipe water distribution) problem, on this point, To a large extent, in fact, because the closed cooling tower equipment on the nozzle outlet debris, nozzle off or the nozzle outlet pressure is too low and other related causes.
Then, when it comes to the closed cooling tower water temperature is relatively high, in general, in fact, because the amount of circulating water is more or less the amount caused by air flow, for its corresponding treatment method, in terms of its large extent In fact, it is in a very large extent, in fact, can play a regulation of water or adjust the blade installation angle, then, that is, pay attention to check its filler.
Then, on the closed cooling tower problems, in fact, that is, including the fan will be abnormal vibration phenomenon, in view of this, it is actually installed in the installation of bolts will be loose, followed by its fan on the impeller That is, there will be an imbalance in the phenomenon of its axis bending in a large extent, in fact, it will be directly caused by the abnormal vibration of the phenomenon of the fan.
On the above phenomenon, we are in fact to a large extent, it should be to pay attention to re-fastening the operation of the bolt, followed by, to a large extent, in fact, it is necessary to pay attention to check each blade installation bias is Not in the provisions of the range, re-pay attention to correct its static balance, replace the drive shaft can effectively solve the problem.
Finally, the closed cooling tower appears in the phenomenon of failure to face the gearbox occurred in the abnormal sound phenomenon, whether it is gear wear on the swap gear, or bearing damage, we actually have to pay attention Directly to replace the bearing, if it is closed cooling tower gear box on the lack of oil, we actually have to pay attention to add lubricants.